HST™ turbocompressorThe modern and silent HST™ turbocompressor features an advanced design with proven magnetic bearing technology and a high-speed motor driven through a built-in frequency converter.
Improvement in efficiency, reliability and availability
New compressors fulfil a wide range of flow requirements
The plant had recently purchased a competitor’s high-speed turbocompressor to trial. The new high-speed turbocompressor was not all the competitor promised. It could not achieve the required turn-down ratio (i.e. could not meet the minimum flow requirements) and had trouble operating reliably in conjunction with the existing positive displacement blowers. The pulsations caused by the positive displacement compressors created shockwaves in the manifold. These shockwaves interfered with the competitor’s passive air bearing system, causing instability in the rotor.
Having limited local engineering presence the competitor was not able to solve the problems. The required range of flows was 2’700-5’467 Nm³/h. This represents an operational turndown ratio of 50%, and 42% compared with the maximum performance, which is a very wide range for a turbocompressor. With a competitor’s machine failing in the field, it was vital that the Sulzer technology would be superior under the same real-life conditions.
Sulzer’s HST turbocompressors can operate reliably in conjunction with existing positive displacement units. Sulzer has a reference site proving this near Melbourne, so an inspection was arranged for the customer. The original intention was to supply two HST turbocompressors to operate alongside the existing ones. The customer, however, decided that no further trials were required and chose to remove all existing machines and replace them with four new Sulzer HST 20-6000-150 turbocompressors.
The HST turbocompressors were factory tested and then field tested. The results were heavily scrutinized due to the competitive situation. The turbocompressors passed all tests showing that Sulzer delivers what is promised.
- NSW & ACT Area Sales Manager, Sulzer Pumps Wastewater Pty Ltd.Efficient, reliable twenty-first century machines.
- Dramatic increase in efficiency over old PD blowers
- Efficiency, reliability and availability improvement compared to competitor’s high-speed turbocompressor
- Reduced footprint, noise and maintenance costs
- Sulzer’s catalogue claimed performance was achieved in site testing.
The project was a retrofit so it was essential that the solution fitted well into the existing compressor room, making it easy to replace the old, inefficient machines.
Rather than the added expense and complication of a field-installed Master Control Unit PLC, these units are controlled directly by the customer’s existing plant-wide SCADA telemetry system. The system uses the latest MODBUS protocol to ensure fast and reliable communication between the customer’s network and the HST 20 turbocompressors.
4 units HST 20-6000-150 turbocompressor
|Flow rating||2’500 – 7’000 Nm³/h|
|Pressure rating||30-90 kPa|
|Peak total efficiency||76%|
|Peak isentropic efficiency||86%|
|Quantity||3 duty, 1 standby|
|Biological process||Intermittently Decanted Aeration Lagoon (IDAL)|
|Maximun required flow||5’467 Nm³/h (humid)|
|Maximum required pressure||65 kPa|
|Minimum required flow||2’700 Nm³/h (humid)|
|Minimum required pressure||40 kPa|